Download Heatline C28 manual. You have chosen to download this manual. Heatline C28, please click on the PDF link below. The boiler’s ‘Log Book’ must be completed at each Service visit. By means of a manual switch the C24/C28 can be set to operate in one of two operating modes, . Boiler Manuals for the Heatline Compact C28 appliance.
|Published (Last):||19 October 2008|
|PDF File Size:||1.23 Mb|
|ePub File Size:||19.55 Mb|
|Price:||Free* [*Free Regsitration Required]|
If so that usually spoils the motor. Save to your online account What’s this? Release the union connections on the connection pipes, retaining the washers for re-assembly 6. You must log in or sign up to reply here.
Ideal Mini C28
Verify the operation of the condensate pump F83 No water in the installation: Boiler parts Each Heatline boiler is equipped with following additional parts: Save energy Energy saving manuual. Release the connection from gas valve and manifold inlet, retaining the washers for use on reassembly as shown on the picture below 6. Maximum temperature difference reached between return and flow heating. I would consider a boiler change although most of us are a bit heatlie straped at the moment it may be money beter spent.
Re-assemble the boiler in reverse order 7.
How can we help?
Locate the central heating sensor — it is on left side of the combustion chamber on the outlet of the primary heat exchanger as shown on the picture below.
Verify the operation of the condensate pump F27 Flame detection fault Verify the flame detection electrode. Such permission may be obtained by emailing servicevisit vaillant. Is the central heating?
When the system is bled of any air it must be refilled until the pressure shown on the display gauge indicates a system pressure of 1.
Check gas soundness and correct boiler operation.
Buy Heatline Gas Water Boiler Parts | eBay
As air is vented the system pressure may need topping back up to 1. It wants to be fixed very soon or manul afraid thats it as far as the landlord goes with regards to me paying anymore rent!! Re-connect sensing tube and all the electrical leads.
Verify the boards reference F71 Flow heating temperature sensor fault Verify the sensor connections. Replace low water pressure switch. Your appliance can be set to work either on domestic hot water and heating or domestic hot water only.
Verify the fuses connections. The fan is activated at the beginning of each ignition cycle. Remove the two screws which connect mznual heat exchanger to hydraulic circuit 5.
The boiler wouldnt turn off even switching to off, last heatlnie swithced the electric off to it. Flow heating temperature sensor fault. Landlords Landlords cover Landlords repair Landlords insurance. All usable parts like washers, igniters etc will heatlne replaced. Yes, my kanual is: Remove the exchanger from the gap on the left hand side as shown the picture below 6.
We recommend to keep following clearances for ventilation purposes: The engineer said he is going to issue a gas safety certificate as soon as the boiler is done. Re-connect sensing tube and all the electrical leads 7. Your appliance is equipped with a number of safety devices that will lock out your boiler functionality in instances where fault would cause permanent appliance damage or cause health safety heatlnie.
Re-set if necessary the dip switches and the potentiometers to values of the old PCB 8. As you have already saved the maximum of 9 manuals to your online services account you need to delete one of these before you can save another one.
When heating demand is requested, power is on and the thermostats are calling for heat, the boiler fires. RicksterOct 21, Remove the pipe clips on the pipes of heat exchanger 5.
Remove the motor 4.